1
GATE EE 2000
+2
-0.6
The severity of line-to-ground and three phase faults at the terminals of an unloaded synchronous generator is to be same. If the terminal voltage is
$$1.0$$ p.u. and $${Z_1} = {Z_2} = j0.1\,\,$$ p.u.,
$$\,{Z_0} = j0.05\,\,\,\,\,$$ p.u., for the alternator, then the required inductive reacttance for neutral grounding is
A
$$0.0166$$ p.u.
B
$$0.05$$ p.u.
C
$$0.1$$ p.u.
D
$$0.15$$ p.u.
2
GATE EE 2000
Subjective
+5
-0
For the configuration shown in figure, the breaker connecting a large system to bus $$2$$ is initially open. The system $$3$$-phase fault level at bus $$3$$ under this condition is not known. After closing the system breaker, the $$3$$-phase fault level at bus $$1$$ was found to be $$5.0$$ p.u. What will be the new $$3$$-phase fault level at system bus $$3,$$ after the interconnection? All per unit values are on common base. Prefault load currents are neglected and prefault voltages are assumed to be $$1.0$$ p.u. at all buses.
3
GATE EE 2000
+1
-0.3
In a 3-step distance protection, the reach of the three zones of the relay at the beginning of the first line typically extends upto
A
100% of the first line, 50% of the second line and 20% of the third line.
B
80% of the first line, 50% of the second line and 20% of the third line.
C
80% of the first line, 20% of the second line and 10% of the third line.
D
50% of first line, 50% of second line and 20% of the third line.
4
GATE EE 2000
+1
-0.3
In an inverse definite minimum time, electromagnetic type over-current relay, the minimum time feature is achieved because of
A
Saturation of the magnetic circuit
B
Proper mechanical design
C
Appropriate time delay element.
D
Electromagnetic damping.
GATE EE Papers
2023
2022
2021
2020
2019
2018
2013
2012
2011
2010
2009
2008
2007
2006
2005
2004
2003
2002
2001
2000
1999
1998
1997
1996
1995
1994
1993
1992
1991
EXAM MAP
Medical
NEET